Functions and characteristics
|Number of poles||3P, 4P|
|Control||Manual||with toggle/with direct or extended rotary handle|
|Plug-in||front connections/rear connections|
|Electrical characteristics as per IEC60947 and EN60947-2|
|Rated current(A)||In||16,25,32,40,50,63,80,100,125,160,200,250||400,500,630||800, 1000, 1250, 1600|
|Rated insulation voltage(V)||Ui||800|
|Rated impulse withstand voltage(kV)||Uimp||8|
|Rated operational voltage(V)||Ue||AC 50/60Hz, 690V|
|Breaking capacity levels||F N H||N H|
|Breaking capacity (kA rms)
AC 50/60 Hz 380/415 V
|lcu||36, 50, 70||50， 70|
|Service breaking capacity (kA rms)
AC 50/60 Hz 380/415 V
|lcs||36, 50, 70||50， 70|
|Protection||Chart B-1 B-2||Chart C-1|
|Indication and control auxiliaries|
|MX Shunt coil||■||■|
|MN under-voltage coil||■||■|
Overload protection: Thermal protection (lr)
Thermal overload protection based on a bimetal strip providing an inverse time curve l2t, corresponding to a temperature rise limit. Above this limit, the deformation of the strip trips the circuit breaker operating mechanism.
Overload protection has the following characteristics:
Anon-adjustable time delay.
Short-circuit protection: Magnetic protection (Im) Short-circuit protection with a fixed or adjustable pick-up lm that initiates instantaneous tripping if exceeded.
Protection of distribution system
Settings are made using the adjustment dials with fine adjustment possibilities.
Overload protection: long time protection(Ir)
Inverse time protection against overloads with an adjustable current pick-up lrsetusing a dial and a non-adjustable time delay tr.
Short-circuit protection: Short-time protection with fixed time delay(Isd)
Protection with an adjustable pick-up lsd.
Tripping takes place after a very short delay used to allow discrimination with the downstream device.
Short circuit instantaneous protection:(li)
lnstantaneous short-circuit protection with a fixed pick-up.
Protection thresholds and delays are set using the adjustment dials.
Offer standard long time delay setting module.
True rms long-time protection.
Thermal memory: thermal image before and after tripping.
Short-time(rms) and instantaneous protection.
Selection of lt type(ON or OFF) for short-time delay.
On 3-pole circuit breakers, neutral protection is not possible.
On 4-pole circuit breakers, neutral protection may be set using a three-position
switch: neutral unprotected (4P 3d), neutral protection at 0.5lr (4P 3d +N/2) or neutral protection at lr (4P 4d).
Overload indication by alarm LED on the front; the LED goes on when the current exceeds the long-time trip threshold.
A mini test kit or a portable test kit may be connected to the test connector on the front to check circuit-breaker operation after installing the trip unit or accessories.
Overall dimensions&Mounting dimensions
CNSD100 TO 250
TMD magnetic trip units，tripping curves protection of distribution systems
CNSD400 TO 630
CNSD500 TO 1600
Chinese companies become World Cup largest sponsors with $1.4 billion; brands promoted to larger marketArgentina won their third World Cup after beating defending ch...
Moulded case circuit breakers have a wide variety of accessories, and the most common accessories are undervoltage, shunt and auxiliary.But what role will these thre...
SSPD Air Circuit Breaker CNT CNW has get been praised by customers in various countries. It has stable performance and competitive price. In addition, for such heavy...
The shunt release device, an internal accessory of MCCB, opens the mechanism in response to an externally applied voltage signal. It realizes that the electrician ca...