|Item No.||CNT06 to CNT16|
|Number of poles||3/4|
|Rated insulation voltage(V)||Ui||1000|
|Impulse withstand voltage(kV)||Uimp||12|
|Rated operational voltage(V AC 50/60Hz)||Ue||690|
|Suitability for isolation||IEC60947-2|
|Degree of pollution||IEC60664-1 3|
|CNT selection criteria|
|CNT06, CNT08, CNT10, CNT12, CNT16||CNT06, CNT08, CNT10|
|Rated current(A)||630, 800, 1000, 1250, 1600||630, 800, 1000|
|Type of application||Standard applicatons with low short-circuit currents||Applications with medium-level short-circuit currents||Limiting circuit breaker for protection of cable-type feeders or upgraded transformer ratings|
|Icu/Ics at 440 V||42 kA||50 kA||100 kA|
|Icu/Ics at 1000 V||-||-||-|
|Icu/Ics at 500 V DC L/R＜15 ms||-||-||-|
|Positon of neutral||Letf||Letf||Letf|
|Type of MicroLogic control unit||A,E,P,H||A,E,P,H||A,E,P,H|
CNT06 to CNT16
Fixed 3/4-poles device
Drawout 3/4-poles device
This question is easy to answer, mainly from two aspects of voltage and current. The following mainly analyzes the selection of plastic case circuit breakers for dis...
AC contactor is mainly composed of four parts: electromagnetic system, contact system, arc extinguishing device, insulating shell and accessories. In Basics for a Be...
Don't want to be fooled, do you know all about air switches, leakage protectors, and distribution boxes?
So why is it tripping? What should I do when it trips? First of all, we need to know that under normal circumstances, home tripping is divided into two types: air sw...